The Profi-screed staple system is installed onto rigid insulation, then covered with either traditional or liquid screed. Ideal for boilers and heat pumps as the heating water required is just 45 degrees.
Profi-screed staple system using 16mm PEX-AL-PEX or PE-RT pipe installed using staples & staple gun.
The Profi-screed staple system is compatible with low temperature heat sources, such as ground or air source heat pumps. The pipe spacing can be reduced or increased depending on the heat loss of the building and the water temperature being supplied by the heat source.
We offer fully designed heating and ventilation systems for todays new and refurbished homes.
Get a free quotation for underfloor heating, ventilation or both.
Installing this system:
Installation starts after the insulation layer has been fitted to the subfloor. A membrane (not supplied) is installed first if a liquid screed is to be used, containing the screed above the insulation. The edge isolation (supplied) is fitted around all perimeter walls, creating a thermal break between the floor and the outside walls.
Pipework is stapled directly into position following the CAD pipe layout diagram (provided). Flow pipes should be fitted with conduit (supplied) to reduce heat loss between manifold and the room to be heated.
Suitable Floor Coverings
- Carpets with 1.5 tog or lower
- Structural timber (18-25mm)
- Polished concrete
This system can be designed with the following average pipe spacing’s.
The following items are included in this system:
- Underfloor heating manifold – pre-assembled
- Pipe staples
- Edge isolation with polythene DPM overlap
- Pipe clips
- Thermostats for each room
- System control box
- CAD pipework drawing
- Electrical wiring guide – first fix
- Electrical wiring guide – second fix
- Installation manual
- Telephone and email